Welcome To The ACHR News Troubleshooting Page
On this exclusive Air Conditioning Heating Refrigeration News page on our site, you’ll find the solutions to the troubleshooting problems published in ACHR News Extra Edition.
Once you’ve reviewed the problem in Extra Edition and checked the answer we present here, feel free to use the submission form below to send us comments or suggestions. We update this page regularly, and we can add your comments to the archived problem answers if you give us permission to do so.
You can also use the submission form to enter our contest by letting us know about specific troubleshooting situations you’ve encountered and solved.
If your submission winds up being the basis for a troubleshooting problem published in Extra Edition, we’ll send you a courtesy copy of the technician training DVD “Electrical Troubleshooting & Schematics for Electromechanical and Electronic Systems: Schematic Symbols and Translating What They Mean”, a $60.00 value.
For more information on ACHR News and Extra Edition, click HERE
May 8, 2017 Issue Answer:
Our test procedures at the indoor coil showed both a higher-than-normal static pressure differential and temperature drop, proving that the coil needs to be cleaned.
June 5, 2017 Issue Answer:
The initial diagnosis is incorrect. The source of the problem is the check valve that is leaking into the indoor coil.
July 10, 2017 Issue Answer:
Two possibilities in this case are a failed thermostat or a problem with the thermostat wiring that is preventing a circuit to the ‘O’ connection on the control voltage terminal board. Without 24-volts applied to this terminal, the reversing valve solenoid isn’t energized, preventing the system from shifting to the cooling mode.
August 7, 2017 Answer:
The component that is suspect is the condenser fan motor. The proper current draw for this motor (part # 621911) is 1.4 Amps. The lower-than-normal current draw indicates that the motor is failing. Intermittently, the motor overheats and stops, the compressor kicks off on overload and attempts a short cycle re-start, which results in a blown fuse.
September 4, 2017 Answer:
What we need to do is correct the reverse polarity power supply problem. Our meter tests showed that the wiring to the equipment is showing a 115V reading from the neutral side of the wiring system to ground, and a 0-V reading from the hot side of the wiring system to ground.
October 9, 2017 Answer:
We need to correct the wiring on the contactor. When it was installed, the L1 and L2 connections were reversed.
ACHR News Troubleshooting Contest Submission Form
Attention HVACR Service Managers & Service Company Owners…..If You Need Materials For Your In-House Technician Training Programs, Click HERE For Information About Our Training DVD’s.